Generac 0G10010SRV Solenoid Coil Plunger Set For RTS Series 100A, 150A & 200A Transfer Switches
This solenoid coil plunger set is normally damaged by brown out conditions that cause low utility voltage to burn up the upper transfer coil. Could also be damaged by a bad limit switch. Cause should be investigated before replacement so that new coil and plunger set is not damaged during transfer.
If the damage is extensive enough, you can order a complete 150/200A contactor assembly here: Generac 0L2911/0D9618 Complete 200A Transfer Contactor Assembly
Was used in all of the 100A, 150A & 200A Generac/Honeywell R series switches including:
RTSC200A3, RTSW200A3, RTSX200A3, RTSD200A3, RTSS200A3, RTSJ200A3, RTSY200A3, RTSY150A3, RXSW200A3, RXSW150A3, RTSR200A3, RTSW150A3, RTSG150A3, RTSG200A3, RTSK200A3, RTSK150A3, RTSM150A3, RTSM200A3, RTSQ150A3, RTSQ200A3, RXSK200A3, RTSM200A3, RXSM200A3, RTSC100A3, RTSW100A3, RTSX100A3, RTSD100A3, RTSJ100A3, RTSY100A3, RXSW100A3, RTSR200A3, RTSG100A3, RTSK100A3, RTSM100A3, RTSQ100A3, RXSK100A3, RTSM100A3, RXSM100A3, and many others!
Generac replacement parts will also usually fit the following Generac branded generators: Honeywell, Guardian, Siemens, Carrier, Watchdog, Centurion, Eaton & Bryant.
If you need Generac generator troubleshooting support, please visit our interactive forum